See all 311 complaints about this building in a rental report
A violation is issued to a building when a city inspector from
NYC's Department of Housing Preservation and Development validates and confirms a complaint made to 311.
The violations listed below are open violations that have yet to be addressed or have not been confirmed
as resolved by the city.
This building has a total of 6 violations which is 0.05 violations per unit for their entire portfolio.
That is better than the city average, which is 0.81 violations per unit.
Non-Hazardous violations (i.e. no peephole on a door, or no street # on the building)
Immediately Hazardous (i.e. rodents, inadequate heat or hot water)
Approval DateDescriptionCurrent Status
Nov 02, 2022§ 27-2013 adm code paint with light colored paint to the satisfaction of this department at ceiling in the 3rd room from north located at apt 8l, 8th story, 5th apartment from north at eastFirst no access to re- inspect violation
May 12, 2019§ 27-2045 adm code post a proper notice of smoke detector requirements, in a form approved by the commissioner, at or near the mail box missing at public hall, 1st storyFalse certification
Frequently Asked Questions
Be the first to ask a question!
Water Pressure: 5
Pest Control: 2
Noise Levels: 4
Owner Responsiveness: 5
Garbage Management: 5
60% of renters recommend this building
60% of renters approve of this owner
Rents and Deposits
95% of renters received their security deposits back
It HAS NOT been reported if this building accepts electronic rent payments.
No heat and hot water for months; sketchy area
This place has some of (c) openigloo the most r...
For over 6 months, we (c) openigloo had intermi...
Lived here, meh
Got a cheap covid deal (c) openigloo and was wo...
Raised rent 77% so I (c) openigloo moved out an...