239 Putnam Avenue,
Brooklyn, NY 11216
No reviews yet
Building Open Data
Built in 1901
1 Year Bedbug History: No
Landlords in NYC are required to file an annual bedbug report with the city and state whether the building has had a bedbug infestation in the past year. We found no recent bedbug reports from these city filings.
Litigation History: No
Litigation history is pulled from NYC housing court records. There are no recorded housing litigations associated with this property from the past 10 years. This information does not include non-housing court cases, such as small-claims cases
Eviction information is pulled from NYC housing court records. There are no legally registered evictions associated with this property.
Rent Stabilized Units: No
We look at annual DHCR registrations to determine if a building has rent-stabilized units. It is possible that a landlord missed an annual registration and therefore the info is not reflected on openigloo. We update this data when the city updates their records. Learn more about rent-stabilizationhere
Once you submit an anonymous review for one of your rental experiences, you will gain access to the entire openigloo platform
Do you have a photo of this building?
A violation is issued to a building when a city inspector from NYC's Department of Housing Preservation and Development validates and confirms a complaint made to 311. The violations listed below are open violations that have yet to be addressed or have not been confirmed as resolved by the city.
This building has a total of 35 violations which is 17.5 violations per unit for their entire portfolio.
That is worse than the city average, which is 0.59 violations per unit.
Non-Hazardous violations (i.e. no peephole on a door, or no street # on the building)
Hazardous violations (i.e. smoke detector issues, inadequate lighting)
Immediately Hazardous (i.e. rodents, inadequate heat or hot water)
Approval DateDescriptionCurrent Status
2021-05-10Section 27-2005 adm code repair the broken or defective plastered surfaces and paint in a uniform color ceiling in the room located at b-room 7, 3rd story, 1st b-room from east at southNov sent out
2020-12-03Section 26-1103 admin. code: post and maintain a proper notice on wall of the entrance story in english and spanish on the availability of the agency?s housing information guide. a sample notice can be found at www.nyc.gov/hpd. at public hall, 1st storyInvalid certification
2020-12-03Section 27-2045 adm code post a proper notice of smoke detector requirements, in a form approved by the commissioner, at or near the mail box missing at public hall, 1st storyInvalid certification
2020-12-03Section 27-2013 adm code paint with light colored paint to the satisfaction of this department ..the ceiling and all walls at public hall, 3rd storyInvalid certification
2020-12-03Section 329, m/d law and dept. rules and regs. provide a completed certificate of inspection visits in a proper frame at or near mailboxes, bottom edge of frame between 48-62 inches above floor missing at public hall, 1st storyInvalid certification
2020-12-03Section 27-2104 adm code post and maintain a proper sign on wall of entrance story showing the registration number assigned by the department and the address of the building. at public hall, 1st storyInvalid certification
2020-12-03Section 300 m/d law file plans and application and legalize the following alteration or restore to the legal condition existing prior to the making of said alteration ..suspended acoustical tiles at ceiling in the bathroom located at b-room 3fl, 3rd storyInvalid certification
2020-12-03Section 27-2046.1 hmc: post a proper notice of carbon monoxide detecting device requirements, in a form approved by the commissioner, in a common area of a class a multiple dwelling near inspection certificate or provide notice to tenants in a private dwelling. at public hall, 1st storyInvalid certification
2020-12-03Section 27-2013 adm code paint with light colored paint to the satisfaction of this department at all walls in the bathroom located at b-room 3fl, 3rd storyInvalid certification
2020-12-03Section 27-2005 adm code properly repair with similar material the broken or defective vinyl floor tiles at public hall, 3rd storyInvalid certification
2020-12-03Section 27-2005 hmc: post, in a form approved by the commissioner, and maintain a notice in a common area of the building regarding the procedures that should be followed when a gas leak is suspectedInvalid certification
2020-10-25Section 27-2013 adm code paint with light colored paint to the satisfaction of this department ceilings and all walls at all stories at public hallInvalid certification
2020-10-25Section 27-2026 adm code reset, so as to secure a proper and tight connection, the water closet bowl , at community bathroom, 3rd storyInvalid certification
2020-10-22Section 27-2005 adm code repair the broken or defective plastered surfaces and paint in a uniform color all walls at community bathroom, 3rd storyNov sent out
2020-10-22Section 27-2013 adm code paint with light colored paint to the satisfaction of this department the ceiling at public hall, 3rd storyNov sent out
2020-10-22Section 27-2005 adm code repair the broken or defective plastered surfaces and paint in a uniform color the ceiling in the room located at b-room 3, 3rd story, 1st b-room from east at southNov sent out
Property Owners and Associates
Site Manager, Owner
Property Owner Open Data
Litigation History: No
Frequently Asked Questions
Be the first to ask a question!
Water Pressure: 5
Pest Control: 2
Noise Levels: 4
Owner Responsiveness: 5
Garbage Management: 5
60% of renters recommend this building
60% of renters approve of this owner
Rents and Deposits
95% of renters received their security deposits back
It HAS NOT been reported if this building accepts electronic rent payments.
No reviews yet