Property Owner Open Data
Litigation History: Yes
A violation is issued to a building when a city inspector from NYC's Department of Housing Preservation and Development validates and confirms a complaint made to 311. The violations listed below are open violations that have yet to be addressed or have not been confirmed as resolved by the city.
This owner/manager has a total of 47 violations which is 0.81 violations per unit for their entire portfolio.
That is worse than the city average, which is 0.59 violations per unit.
Non-Hazardous violations (i.e. no peephole on a door, or no street # on the building)
Hazardous violations (i.e. smoke detector issues, inadequate lighting)
Immediately Hazardous (i.e. rodents, inadequate heat or hot water)
Approval DateDescriptionCurrent Status
2017-09-12Section 27-2005 adm code replace with new the missing electric outlet safety cap at west wall at public hall, 1st storyNot complied with
2017-09-06Section 329, m/d law and dept. rules and regs. provide a completed certificate of inspection visits in a proper frame at or near mailboxes, bottom edge of frame between 48-62 inches above floor incorrect frame at public hall, 1st storyNot complied with
2015-04-27Section 27-2013 adm code paint with light colored paint to the satisfaction of this department all peeling paint surfaces in the foyer , the 2nd bathroom from east at north, the 3rd room from east at north, the 2nd room from east at south located at apt 5d, 5th story, 4th apartment from south at westNov sent out
2014-10-06Section 27-2013 adm code paint with light colored paint to the satisfaction of this department all peeling paint surfaces in the kitchen , the bathroom , the 2nd room from east at north located at apt 5d, 5th story, 4th apartment from south at westNot complied with
2014-09-24Section 27-2013 adm code paint with light colored paint to the satisfaction of this department east wall at cellarNov sent out
2014-09-24Section 300 m/d law file plans and application and legalize the following alteration or restore to the legal condition existing prior to the making of said alteration drop ceiling installed at cellarNov sent out
2014-09-24Section 27-2013 adm code paint with light colored paint to the satisfaction of this department ceiling at cellarNov sent out
Water Pressure: 5
Pest Control: 2
Noise Levels: 4
Owner Responsiveness: 5
Garbage Management: 5
60% of renters recommend this building
60% of renters approve of this owner
Rents and Deposits
95% of renters received their security deposits back
It HAS NOT been reported if this building accepts electronic rent payments.
No reviews yet