A violation is issued to a building when a city inspector from NYC's Department of Housing Preservation and Development validates and confirms a complaint made to 311. The violations listed below are open violations that have yet to be addressed or have not been confirmed as resolved by the city.
This owner/manager has a total of 15 violations which is 0.88 violations per unit for their entire portfolio.
That is worse than the city average, which is 0.59 violations per unit.
Non-Hazardous violations (i.e. no peephole on a door, or no street # on the building)
Hazardous violations (i.e. smoke detector issues, inadequate lighting)
Immediately Hazardous (i.e. rodents, inadequate heat or hot water)
Approval DateDescriptionCurrent Status
2017-11-15Section 27-2005 hmc: post, in a form approved by the commissioner, and maintain a notice in a common area of the building regarding the procedures that should be followed when a gas leak is suspected at public hall, 1st storyNov sent out
2017-11-15Section 329, m/d law and dept. rules and regs. provide a completed certificate of inspection visits in a proper frame readily accessible for signature, bottom edge of frame between 48-62 inches above floor at ,, at public hall, 1st storyNov sent out
2016-07-25Section 27-2104 adm code post and maintain a proper sign on wall of entrance story showing the registration number assigned by the department and the address of the building.Nov sent out
2016-07-25Section 26-1103 admin. code: post and maintain a proper notice on wall of the entrance story in english and spanish on the availability of the agency''s housing information guide. a sample notice can be found at www.nyc.gov/hpd.Nov sent out
2016-07-25Section 27-2046.1 hmc: post a proper notice of carbon monoxide detecting device requirements, in a form approved by the commissioner, in a common area of a class a multiple dwelling near inspection certificate or provide notice to tenants in a private dwelling.Nov sent out
2016-07-25Section 27-2045 adm code post a proper notice of smoke detector requirements, in a form approved by the commissioner, at or near the mail boxNov sent out
2016-07-25Section 329, m/d law and dept. rules and regs. provide a completed certificate of inspection visits in a proper frame at or near mailboxes, bottom edge of frame between 48-62 inches above floorNov sent out
Water Pressure: 5
Pest Control: 2
Noise Levels: 4
Owner Responsiveness: 5
Garbage Management: 5
60% of renters recommend this building
60% of renters approve of this owner
Rents and Deposits
95% of renters received their security deposits back
It HAS NOT been reported if this building accepts electronic rent payments.
Absolutely Not - RUN
Roof top access.
Awful landlord (Martin) - a nightmare to communicate with and refuses to take action (even on safety related issues) until you withhold rent and/or threaten to work with a lawyer. Unsafe area - building across the street had multiple fatal drive by shootings last year. Squatters in the alley way and often inside the building. Tried to keep our security deposit until we threatened going to court.
Advice to owner:
Do not let Martin manage this property. Make the building safer and cleaner.