Property Owner Open Data
Litigation History: Yes
A violation is issued to a building when a city inspector from NYC's Department of Housing Preservation and Development validates and confirms a complaint made to 311. The violations listed below are open violations that have yet to be addressed or have not been confirmed as resolved by the city.
This owner/manager has a total of 16 violations which is 0.57 violations per unit for their entire portfolio.
That is better than the city average, which is 0.59 violations per unit.
Non-Hazardous violations (i.e. no peephole on a door, or no street # on the building)
Hazardous violations (i.e. smoke detector issues, inadequate lighting)
Immediately Hazardous (i.e. rodents, inadequate heat or hot water)
Approval DateDescriptionCurrent Status
2020-09-22Section 53, 187, 231 m/d law and department rules and regulations. provide a shoe properly secured to bottom of string of dropladder broken shoe at front stack at fire escapeNov sent out
2019-02-27Section 27-2013 adm code paint with light colored paint to the satisfaction of this department the east wall at public hall stairs, 1st storyNov sent out
2019-02-27Section 27-2104 adm code post and maintain a proper sign on wall of entrance story showing the registration number assigned by the department and the address of the building. at public hall, 1st storyNov sent out
2019-02-27Section 27-2005 adm code replace with new the broken or defective glass pane on door at building entrance at public hall, 1st storyNov sent out
2019-02-27Section 27-2013 adm code paint with light colored paint to the satisfaction of this department the north and south wall at public hall, 1st storyNov sent out
2019-02-27Section 27-2005 adm code properly repair with similar material the broken or defective fire retardant material, north and south wall at public hall, 1st storyNov sent out
2019-02-27Section 27-2005 adm code properly repair with similar material the broken or defective fire retardant material at east wall at public hall stairs, 1st storyNov sent out
2017-06-13Section 27-2005 hmc: post, in a form approved by the commissioner, and maintain a notice in a common area of the building regarding the procedures that should be followed when a gas leak is suspected at public hall, 1st storyNov sent out
Water Pressure: 5
Pest Control: 2
Noise Levels: 4
Owner Responsiveness: 5
Garbage Management: 5
60% of renters recommend this building
60% of renters approve of this owner
Rents and Deposits
95% of renters received their security deposits back
It HAS NOT been reported if this building accepts electronic rent payments.
No reviews yet